Product category: PLCs – Omron – C – Omron CH-LK (CHLK) This unit is fully tested prior to. Q: Can CH-LKV1 Host Link Unit be used with CS1-series Programmable Controllers?. CH Units that use the CPU bus, SYSMAC LINK Unit, CHW-SLK23/24 ( wired) CHW-SLK13/14 (optical). Controller Link Unit, CHW-CLK21 (wired ).
|Published (Last):||7 October 2015|
|PDF File Size:||6.55 Mb|
|ePub File Size:||15.46 Mb|
|Price:||Free* [*Free Regsitration Required]|
C200g up for a new account in our community. You should verify the cable. Try to put il elsewhere. Be careful what you plug into it. Share this post Link to post Share on other sites. The long port at the bottom is for a 3G2A6-LK Posted 14 Nov edited. Maybe the backplane is bad. This may or may not be an issue if they are mismatched It is a pre-Alpha series. Lk20 the information you have provided, there is no way for us to tell.
The PLC configuration does not matter.
For communications with CX Programmer, you should be able to use the same cable that is ,k201 connected to you custom application. The manual in the link I posted above describes these functions. Help me with ch-lk Started by sokhanh13 Nov C Series Host Link Units.
Omron C200H-LK201-V1 Industrial Control System
On the older ones, it was only intended for the hand held programmer. PCMRthat Data will have to be reentered into the appropriate locations. The dip witches in the host link are correct but still not 2c00h.
I did notice that c20h0 of his modules are in the restricted slots. One of the other old school guys will have to answer this one. Posted 13 Nov What is the part number of your back plane? I have blown internal circuit board fuses on some of the older CH’s by trying to use that port.
Create an account or sign in to comment You need to be a member in order to leave a comment Create an account Sign up for a new account in our community. Posted 13 Nov edited. All the configuration is done with the LK switches. This is common Omron serial settings.
Omron SYSMAC C200h-lk201 Host Link Unit C200HLK201
You need to be a member in order to leave a comment. If it is not blinking then you have lm201 bad connection. Jay and Bob, Thanks for the feedback! The 25 pin connector would run into the bottom of those peripheral units if you used these slots. Posted 21 Nov Remove all the modules from the rack and try the Host Link in another slot.
Help me with ch-lk – Omron –
Posted 16 Nov edited. Sign In Sign Up. On the CPU, led “run” is green. Maybe the PLC power supply is bad. I have checked the cable carefullly, the cable should be ok. Try turning if OFF. I have tried with an ch-lkv1 but everything is the same. I have replaced ch-lkv1 by ch-lk and everything is the same. Thank you for your explaination, I have tried with pin 3 on the back OFF but still cannot conect.
Edited 15 Nov by sokhanh. The restriction is strictly cc200h. After revisiting this I found conflicting information in the manuals. It’s on page 9 in the manual. The DIP switch front are 0;0;5;2 back are off;off;on;off;0v Please help me! Posted 15 Nov Sign in Already have an account? I also tried with this cable Lj201 Coputer But there’s still no RCV light Please help me! Neither of them are V1’s. I did an internet search for your PLC.